Clear sailing ahead.
Clear sailing ahead.
Clear sailing ahead.
Dec 18 2014, 3:39 PM (352 w, 6 d)
Completed auto-reimage of hosts:
This is complete
Bullseye installer giving me "Failed to load ldlinux.c32"
default username is admin and password is YourPaSsWoRd
I have SONIC on all 4 switches .
Shipped out the CPI PDU today
I checked the server today i have no errors showing on A1 closing this task . IF we have the error again please reopen the task.
fist let us swap A1 with B1
and see if we still have the error on A1. Memory swap complete and IDRAC upgrade from 2.50 to 2.80. i will leave the task open for now until next week.
this is complete on my end . Let me know if you have any issues.
papaul@fasw-c-codfw# run show interfaces ge-0/0/5 terse
Interface Admin Link Proto Local Remote
ge-0/0/5 up up
ge-0/0/5.0 up up eth-switch
Have in a temporary cable ID for this. I will remove the serial cable once configuration is done.
It was a loose power cord . Fixed
it looks like mw2383 is happy now can we close this task ?
Please see below for the issue we found. The Power cap was enable setting the cap limits at 128watts below the recommended range of 213-355 watts) which was less then what both CPU's needed. I disable the Power cap limit like on mw2384. We can try to put back the server in production so we can see if this resolve the issue.
Looking at the log today i have
thank you i will open a case with Dell
@willy I am using a personal Cisco roll over cable that connects the device to the console server . This was done so that the device can be configured. once the configuration done I am planning on removing the cable.
Both test PDU's removed and old PDU"s back in place.
I open ticket #2045424 with CY1 to unplug both test PDU's in D8
for tomorrow. We will be putting back the old PDU for now until we received another test PDU.
Received the replacement switch. Rack in C1 U43. setup the mgmt password same as the server mgmt password. Update Netbox with new serial number.
CamScanner 08-10-2021 11.13.pdf273 KBDownload
thank you for the update Willy knows already about those. Those are line cards, we can not put asset tags on line cards.
Your replacement part associated with RMA R200361905 Item # 100 has been successfully shipped. Details of which are provided below.
I as far as i know I removed the old faulty device, replaced it with this on, connected the console, power and network to the device, that's all
Resolving this task since all 3 links on lvs2010 moved to asw-a4,asw-b4 and asw-c4
I can set up the interface on asw-a4-codfw
do you have time today 10am CT to move only
lvs2010 ens2f1np1 xe-2/0/44 asw-a4-codfw from A2 to a4 xe-4/0/47
can you try to get the system back again in service? The system has 2 CPU's so it will be difficult to tell which CPU is bad if we do not have any logs telling which CPU is having issues. I will like to have the system back online so i get take a look as well when the the system is having issues. I think Rob did all the firmware upgrade which is great. If we do not find anything I will open a case with DELL
Dear Juniper Networks Customer,
thank you I have all the information needed. I will do my site audit and get back with you next week to setup a day and time to start moving those links
thank you. What about lvs2007 ens3f1np1? Actually it is connected to d7 and you want it to be moved to C7 or lvs2007 ens3f0np0 is already connected to C7
Ok understood. Please provide me with the configuration you want in a table like above for each server which NIC connects to which switch and i can do my site audit on how best to re-route those links.
if my understanding is right you want for example lvsX NIC 1 to switch asw-a2 NIC 2 to switch asw-a7 (2 switches in ROW A) and NIC 3 to switch asw-b2 and NIC 4 to swirch asw-b7 (2 switch in ROW B) and so on ?
the only limitation i cans see is the number of NIC ports on each server. Each server has 4 NIC's each NIC connected to 1 row on 1 switch. If we do keep the existing configuration then we will have to add another 4 ports NIC in each server so that each server can have 2 connections on each row.
Reset and upgrade IDRAC. Server is back up online.
Shipped out faulty line card today. Tracking information below
FPC0 S/N updated in Netbox
Reset IDRAC , server is back up